Open as PDF
CAUTION: The cabinet is heavy (see page 63): 1) Dell strongly recommends to remove the battery tray from the
UPS before lifting. 2) Lifting the cabinets into the rack requires a minimum of two people.
CAUTION: Removing the batteries should be performed or supervised by personnel knowledgeable about
batteries and the required precautions. Keep unauthorized personnel away from batteries.
CAUTION: If installing an optional EBM, install the EBM directly below the UPS.
NOTE: Mounting rails are required for each individual cabinet.
To install the UPS and optional EBM in a rack:
1 Remove the internal battery tray from the UPS:
Loosen the thumbscrew on the metal battery cover, slide the cover to the right, and open (see
Figure 8. Opening the Metal Battery Cover